POWERVAR_CX_SER(8)
==================

NAME
----

powervar_cx_ser - Driver for Powervar UPM Series UPS equipment with Serial connection

SYNOPSIS
--------

*powervar_cx_ser* -h

*powervar_cx_ser* -a 'UPS_NAME' ['OPTIONS']

NOTE: This man page only documents the hardware-specific features of the
Powervar driver.  For information about the core driver, see
linkman:nutupsdrv[8].

SUPPORTED HARDWARE
------------------

This driver supports the Powervar UPM UPS family (devices with serial
port connection). For USB connected UPM Series devices, see also
linkman:powervar_cx_usb[8].

EXTRA ARGUMENTS
---------------

This driver supports the following optional settings in the
linkman:ups.conf[5] file:

*startdelay*='num'::
Change startup delay time from 1 second default.

*offdelay*='num'::
Change shutdown delay time from 0 second default.

*disptesttime*='num'::
Change display test time from the 10 second default.

INSTANT COMMANDS
----------------

This driver supports the following Instant Commands
(see linkman:upscmd[8]):

All GTS and UPM UPS units
~~~~~~~~~~~~~~~~~~~~~~~~~

*beeper.disable*::
Disable the UPS beeper.

*beeper.enable*::
Enable the UPS beeper.

*beeper.mute*::
Temporarily mute the UPS beeper.

*shutdown.return*::
Turn off the load possibly after a delay and return when power is back.

*shutdown.stop*::
Stop a shutdown in progress.

*shutdown.reboot*::
Shut down the load briefly while rebooting the UPS.

*shutdown.stayoff*::
Turn off the load and remain off.

*test.battery.start.deep*::
Start a "deep" battery test.  This test runs the UPS until the low
battery point and then returns to the AC line.

*test.battery.start.quick*::
Start a "quick" battery test.  The default time is 2 minutes.  This
time can be set in the *ups.conf* file.  See *testime* above.

*test.battery.stop*::
Stops a battery test that is in progress.

*test.failure.start*::
Starts a simulation of an input power failure.

*test.failure.stop*::
Stops a simulation of an input power failure.

All UPM UPS units
~~~~~~~~~~~~~~~~

*test.panel.start*::
Start testing the UPS panel.

*reset.input.minmax*::
Reset minimum and maximum input voltage status.

Writable Variables
------------------

See linkman:upsrw[8] to see what variables are writable for the UPS.


AUTHORS
-------

* Bill Elliot <bill@wreassoc.com>

SEE ALSO
--------

For USB connected GTS and UPM Series devices, see linkman:powervar_cx_usb[8].

The core driver:
~~~~~~~~~~~~~~~~

linkman:nutupsdrv[8]

Internet resources:
~~~~~~~~~~~~~~~~~~~

The NUT (Network UPS Tools) home page: https://www.networkupstools.org/
